### Recent Blog Entries

• Mar 25
Posted by jack black
You may have heard of silicone dolls or sex dolls, you may have seen documentation or read an article about an owner. There is a lot of speculation about the love for mini sex doll and the content that people use, but the answer is different for every doll manufacturer and customer. So wha...
•   When generator sets operate in parallel, the engine speed governor of each generator set determines the proportional sharing of the total active power requirements (kW) of the system.  For two systems to be paralleled, each must have the following matching characteristics for correct...
• Feb 1
Posted by Reynaldo Danilo
Load management systems may prioritize loads based on the load type or importance. Load importance may vary widely depending on the application and facility, but often fall generally within one of the following categories: Non-Critical Loads These are loads that, if removed, will...
• Jan 26
Posted by Hameedullah Ekhlas
When the system is totally isolated from the ground circuit, except through indicating, measuring or protective devices, which are normally grounded and possess a high impedance to ground, the ground fault factor     This may become higher, depending upon the circuit...
View All

Test

## Transformer Fault current calculator

• TRANSFORMER FAULT CURRENT

Calculating the short Current when there is a Transformer within the circuit. Every transformer has “ %” impedance value stamped on the nameplate. Why is it stamped? it's stamped because it is a tested value after the transformer has been manufactured. The test is as follows: A voltmeter is connected to the primary of the transformer and thus the secondary 3-Phase windings are bolted in conjunction with an ampere meter to read the worth of current flowing within the 3-Phase bolted fault on the secondary. The voltage is mentioned in steps until the secondary full load current is reached on the ampere meter connected on the transformer secondary.

So what does this mean for a 1000KVA 13.8KV – 480Y/277V. First you'll need to know the transformer Full Load Amps Full Load Ampere = KVA / 1.73 x L-L KV

FLA = 1000 / 1.732 x 0.48

FLA = 1,202.85

The 1000KVA 480V secondary full load ampere is 1,202A.

When the secondary ampere meter reads 1,202A and thus the first Voltage Meter reads 793.5V. The percent of impedance value is 793.5 / 13800 = 0.0575. Therefore;

% Z = 0.0575 x 100 = 5.75%

This shows that if there was a 3-Phase Bolted fault on the secondary of the transformer then the utmost fault current that might flow through the transformer would be the ratio of 100 / 5.75 times the FLA of the transformer, or 17.39 x the FLA = 20,903A

Based on the infinite source method at the primary of the transformer. a fast calculation for the utmost Fault Current at the transformer secondary terminals is FC = FLA / %PU Z FC = 1202 / 0.0575 = 20,904A

This quick calculation can assist you identify the fault current on the secondary of a transformer for the aim of selecting the proper overcurrent protective devices which can interrupt the available fault current. the most breaker that's to be installed within the circuit on the secondary of the transformer possesses to possess a KA Interrupting Rating greater then 21,000A. remember that feeder breakers should include the estimated motor contribution too. If the actual connected motors aren't known, then assume the contribution to be 4 x FLA of the transformer. Therefore, during this case the feeders would be sized at 20.904 + (4 x 1202 = 25,712 Amps

Utility MVA at the first of the Transformer

MVAsc = 500MVA

Transformer Data

13.8KV - 480Y/277V

1000KVA Transformer Z = 5.75% MVA Value

1000KVA / 1000 = 1 MVA

MVA Value = 1MVA / Zpu = 1MVA / .0575 = 17.39 MVA

Use the admittance method to calculate Fault Current 1 / Utility MVA + 1 / Trans MVA = 1 / MVAsc

1 / 500 + 1 / 17.39 = 1 / MVAsc

0.002 + 0.06 = 1/ MVAsc MVAsc = 1 / (0.002 + 0.06) MVAsc = 16.129

FC at 480V = MVAsc / (1.73 x 0.48) FC = 16.129 / 0.8304

FC = 19.423KA FC = 19, 423 A

Reference:

• Blakley
• Simple Methods for Calculating Short Circuit Current Without a Computer By Dennis McKeown, PE